These are the steps to detect a newly installed SC20Cont or to change the serial number on your device. Ensure the inverter is in stop or remotely set it to stop using the "SpntRemEna" parameter to "Stop".
Begin by logging into the inverter
Check to see if you have communications with the board. You should see a green check mark next to the inverter. If you see a grey field with three dots, this means that the board needs to be detected.
Example with a grey "..." no communications with the control board
Example with a green "check" indicating communications are valid with the control board
Click on the service tab in the top left-hand corner. Use the second button down to "Delete" the "Unit descriptions."
Navigate to the "Data" tab and then "Detection" tab. Click "Start detection" on whichever communications port you need to detect. In most cases it will be COM3.
The inverter will work through detecting the new board or the new serial number.
Now you can navigate back to "Data" and click on the serial number with the green check next to it. Select the parameter tab and now you can change the "Serial Number" parameter to the correct serial number.
Afterwards, it's always best to power cycle the inverter. You can simply use the "PwrSupRs" parameter.
Once the inverter comes back online, begin at the beginning again. Delete unit descriptions, redetect, and the inverter should update with the new serial number.