Fault Description / Instruction:
- . Measure voltage at DC terminals in wiring boxand compare with reading in “Measurement Data”menu. PV voltage must be less than 1000V in open circuit condition
- If display reading is not within 2% of meter reading, replace inverter
- If display reading is within 2% of meter reading,adjust number of panel in the string.